Attenuation - Duct Bend

**Strutt|Mechanical Services|Duct Elements|Bend** inserts attenuation due to bends in ductwork into the active row of the worksheet.

Insertion loss data can be sourced from ASHRAE 1991 (Tables 17, 18 and 19) or the Arup Sound and Vibration in Mechanical Services Design (Blue Book - Tables 14, 15 and 16).

The input required is the characteristic dimension of the duct, width (w) in the same plane as the change in direction of the duct, number of bends and the type of bend (plus the lining thickness, for some calculations).

**Arup Mechanical Services Guide** is based on the SRL book and references octave band attenuation according to the range that the duct width is within.

**ASHRAE (1991)** calculates the attenuation for bends as follows:

- For
__unlined or lined mitred bends without turning vanes__, Strutt calculates based on the product of frequency and bend dimension `f*d` using the values in Table 5.13 ASHRAE 1991 - For
__unlined or lined mitred bends with turning vanes__, Strutt calculates based on the product of frequency and bend dimension `f*d` using the values in Table 5.15 ASHRAE 1991 - For
__unlined radiused bends__, Strutt calculates based on the product of frequency and bend dimension `f*d` using the values in Table 5.14 ASHRAE 1991 - For
__lined radiused bends__, Strutt uses the following equations:

For duct sizes between 6 and 18 inches (150 mm and 450 mm):

`IL*(d/r)^2=0.485+2.094log(f*d)+3.172[log(fd)]^2-1.578[log(fd)]^4+0.085[log(fd)]^7`

For duct sizes between 18 and 60 inches (450 mm and 1500 mm):

`IL*(d/r)^2=-1.493+0.538t+1.406log(fd)+2.779[log(fd)]^2-0.662[log(fd)]^4+0.016[log(fd)]^7`

where:

`f` is the frequency (Hz)

`d` is the duct diameter (in)

`r` is the radius of the bend (in)

`t` is the thickness of the duct lining (in)

**CIBSE** calculates the attenuation for bends as follows:

- For
__unlined or lined mitred bends without turning vanes__, Strutt calculates based on the product of frequency and bend dimension `f*d` using the values in Table 5.6 CIBSE - For
__unlined or lined mitred bends with turning vanes__, Strutt calculates based on the product of frequency and bend dimension `f*d` using the values in Table 5.7 CIBSE - For
__unlined radiused bends__, Strutt calculates based on the product of frequency and bend dimension `f*d` using the values in Table 5.8 CIBSE - For
__lined radiused bends__, Strutt uses the following attenuation values (independent of the bend dimension)

Lining 63 Hz 125 Hz 250 Hz 500 Hz 1 kHz 2 kHz 4 kHz 8 kHz 25 mm 0 2 5 7 10 10 10 10 50 mm 0 5 8 10 13 13 13 13

References:

- Arup, Sound and Vibration in Mechanical Services Design, pp41 - 43
- ASHRAE Algorithms for HVAC Acoustics (1991), p5-9 to 5-13.
- CIBSE Guide B 2005 Section 5.6.4

Comments or suggestions to strutt@arup.com